Information and advice from the air conditioning experts
At Chillaire we pride ourselves on the depth of our information and expertise concerning all aspects of air conditioning, heating and ventilation. If you don’t find the information you are looking for in the sections below, please get in touch and we will be happy to give you some advice.
Legislation relating to Air Conditioning Systems
Current legislation relating to air conditioning systems is summarised below.
Owners/operators of air conditioning and heat pump systems could end up facing serious penalties if they don’t comply with these regulations.
Not being aware of your responsibilities will not prevent the government from imposing financial penalties on anyone found to be in breach of these regulations which have been introduced to improve energy efficiency and reduce damage to the environment from leaking global warming and ozone-depleting gases.
It follows that the owner/operator must bear the cost of complying with the legislation.
Refrigerant leakage checks
Owners/operators of air conditioning systems must:
• Prevent leakage of refrigerant and repair any leaks as soon as possible.
• Arrange proper refrigerant recovery by certified personnel during servicing and disposal.
• Carry out leak checks to the schedule shown below.
• Ensure that only certified competent personnel carry out leakage checks.
• Maintain records of refrigerant usage and of servicing.
The checking frequency varies depending upon the amount of refrigerant in the system as follows:-
• At least annually for systems with 3kg or more of refrigerant.
• At least every 6 months for systems with 30kg or more of refrigerant.
• At least every 3 months for systems with 300kg or more of refrigerant.
• Leakage detection equipment must be installed on systems with 300kg or more of refrigerant and when this is in place, checking frequency requirements are halved.
• When a leak is detected and repaired, a further check must be carried out within one month to ensure that the repair has been effective.
Operators must maintain service records including:
• Quantity and type of refrigerant gases in the system and refrigerant added or recovered.
• Identification of the company or technician carrying out the servicing.
• Dates and results of leakage checks, specifically identifying separate pieces of equipment containing 30kg of refrigerant or more.
It is the operator’s responsibility to ensure that the relevant servicing personnel have obtained the necessary certification which shows they understand the regulations and are competent.
R22 refrigerant is a hydro chlorine fluoride carbon (HCFC) and is used commonly in air conditioning, chillers and industrial refrigerant plant applications.
Due to its ozone depleting properties (ODP) is no longer considered acceptable under the Montreal Protocol.
Production of R22 air conditioning equipment ceased in 2003 and the use of virgin R22 being banned from 01.01.2010.
Reclaimed R22 refrigerant can be used until 01.01.2015 but due to demand this can be very difficult to obtain and very expensive.
New refrigerants and equipment have been developed and the most popular systems operate on refrigerant R410A which has a zero ozone depleting potential and is more energy efficient than the R22 refrigerant equipment. However it has now been realised in the latter years that R41oa has a very GWP and the latest refrigerant to be introduced now is R32 which will replace R410a.
New systems operating on this refrigerant are up to 30% more efficient equating to less energy consumption, lower subsequent energy costs and lower CO2 emissions.
R22 equipment can be used after 01.01.2015 but replacement components will be extremely difficult to obtain and it will be illegal to top up the refrigerant circuit with new or virgin R22 refrigerant
Air Conditioning Energy Inspections
Air-conditioning systems with an effective rated cooling output of more than 12kw must be regularly inspected by an accredited Energy Assessor in order to satisfy the Energy Performance Buildings Directive (EPBD). The inspections must be a maximum of five years apart.
The regulations require the first inspection of air-conditioning systems to be carried out as follows:
• where the effective rated cooling output is more than 250kW the first inspection must happen by 4 January 2009
• for other air-conditioning systems, where the effective rated cooling output is more than 12kW the first inspection must happen by 4 January 2011
• for all ‘new’ systems first put into service on or after 1 January 2008, the first inspection must have taken place within five years of the date when it was first put into service
From 4 January 2011, if the person in control of the air-conditioning system changes and the new person in control is not given an inspection report, the new person in control of the system must ensure the air-conditioning system is inspected within three months of the day that person assumes control of the system.
The effective rated output is the maximum calorific output in kW stated by the manufacturer of the system as deliverable during continuous operation while complying with the useful efficiency indicated by the manufacturer.
One or more air-conditioning units within a building controlled by a single person are considered to comprise a single air-conditioning system for the purposes of the regulations.
This Legislation is mainly intended to apply where air conditioning is provided for the comfort of occupants. It does not apply to process cooling i.e. where air conditioning is provided purely as a requirement for a manufacturing process, or for cooling electronic equipment in unmanned rooms.
Comes into force on 1st January 2013. It introduces minimum energy efficiency requirements for air conditioning systems up to 12kW.
Enhanced Capital Allowance
Enhanced capital allowance (ECA) scheme is designed to encourage businesses to reduce the amount of carbon released into the atmosphere.
The scheme provides an incentive for businesses to invest in energy saving plant and machinery by allowing them to offset their entire investment against taxable profit in the same year as the investment is made.
In order to qualify for the ECA scheme the energy saving investment must meet specific energy efficiency criteria, a list of which is available at www.eca.gov.uk/etl/criteria
Information can also be found on www.eca.gov.uk/etl/find
The energy technology list (ETL) is a definitive list of all products that qualify for the ECA.
The list is regularly updated to ensure that it includes the most energy efficient products currently available.
Because they are a renewable energy technology air source heat pumps can deliver significant energy and carbon savings. They can be included into fuller integrated heating, cooling, hot water, ventilation and heat recovery systems for very complex buildings.
The ECA scheme is open to all UK businesses that pay corporation tax or income tax and is claimed on company’s tax return in the same way as other capital allowances. For details on how to claim can be found at www.eca.gov.uk/etl/claim
Chillaire Group Company Policies
Revision Date: 21st May 2018
(General Data Protection Regulations Document Number: 002)
Information that you may provide us.
Chillaire Limited is a business to business supplier of air conditioning, heating and ventilation equipment, services and support. Chillaire Limited is committed to ensuring that your privacy is protected. Should we ask you to provide certain information by which you can be identified, then you can be assured that it will only be used in accordance with this privacy statement.
Our GDPR Principles:
We will process all personal data fairly and lawfully.
We will only process personal data for specified and lawful purposes.
We will endeavour to hold relevant and accurate personal data, and where practical, we will keep it up to date.
We will not keep personal data for longer than is necessary.
We will keep all personal data secure.
We will endeavour to ensure that personal data is not transferred to countries outside of the European Economic Area (‘EEA’) without adequate protection being in place.
Chillaire Limited may change this policy from time to time and updated copy can be requested at any time. This policy is effective from25th May 2018.
What we collect
Name and job title
Address and contact information including telephone number and email address
What we do with the information we gather
We require this information to understand your needs and provide you with our services, and in particular for the following reasons:
Internal record keeping
Provision of services and aftercare support
We may use the information to improve our products and services
We may periodically send promotional emails about new products, special offers, revised quotations or other information which we think you may find of interest by email using the email address provided by you. You can request to unsubscribe from receiving any emails by replying to email@example.com or by calling our office.
We may contact you from time to time for market research or for quality assurance exercise to complete a questionnaire for quality purposes.
We are committed to ensuring that your information is secure. In order to prevent unauthorised access or disclosure, we have put in place suitable physical, electronic and managerial procedures to safeguard and secure the information we collect.
Other Policies Available upon Request
Health & Safety
Alcohol & Substance Abuse
Working with Asbestos
Chillaire currently has the following vacancies:
Air conditioning installation engineer
We are looking for an air conditioning installation engineer with qualifications or experience essential. Covering mainly the South Birmingham, Sutton Coldfield, Leicestershire, Northamptonshire, Oxfordshire, Coventry and Warwickshire, but going further when required. Need to have experience installing split systems, multi systems and VRV / VRF systems and on occasions you would be assisting our senior engineers or on your own if you have the capability of installing close control systems or chiller systems. Basic salary offered would be subject experience / qualifications plus overtime, vehicle, mobile phone and fuel card.
Air conditioning & heating service engineer
We are looking for an air conditioning and heating engineer with qualifications or experience essential. Need to have experience servicing split systems, multi systems and VRV / VRF systems, close control systems, chiller units, boilers, warm air heaters and radiant tube heaters. Covering mainly the South Birmingham, Sutton Coldfield, Leicestershire, Northamptonshire, Oxfordshire, Coventry and Warwickshire Basic salary offered would be subject experience / qualifications plus overtime, vehicle, mobile phone and fuel card.
Air conditioning engineer & HVAC engineers
Air Conditioning Engineer required anyone with gas fired heating qualifications who has also been working on air conditioning systems and wants to further their career in Air conditioning service and maintenance and obtain their F-Gas certificate. We will provide training and experience. For full details please contact us.
We are also looking for fully qualified full HVAC engineers / multi task engineers. Please contact us for full details.
Good Basic Pay + Overtime + Vehicle + Fuel Card + Mobile Phone + Tools + Uniform + Training
Please complete the following form ensuring the position applied for is clearly noted in the cover letter and attach your CV below.